# POWERMAN-PDU(8)

## NAME

powerman-pdu - Driver for Powerman PDU

## SYNOPSIS

powerman-pdu -h

powerman-pdu -a PDU_NAME [OPTIONS]

Note | This man page only documents the hardware-specific features of the powerman-pdu driver. For information about the core driver, see nutupsdrv(8).

## SUPPORTED HARDWARE

This driver supports a wide range of PDUs through the Powerman project.

This includes various models from APC, Baytech, Cyclades, but also support IPMI and various blade management modules from HP, IBM and Sun.

## EXTRA ARGUMENTS

This driver doesn’t support any optional settings.

## INSTALLATION

This driver may be not built by default. You can build it by installing prerequisites and using `configure --with-powerman=yes`.

## UPS COMMANDS

The following instant commands (see upscmd(8)) are available for each outlet of the PDU, with X standing for the outlet number:

outlet.X.load.on

  Power on the outlet.

outlet.X.load.off

  Power off the outlet.

outlet.X.load.cycle

  Cycle the outlet (power off then power on, possibly with a delay).

## IMPLEMENTATION

The hostname of the Powerman server is specified using the "port" value in ups.conf, i.e.:

    [pdu]
            driver = powerman-pdu
            port = host.example.com:port

The port used to reach powermand is optional if the default port is used.

## KNOWN ISSUES

In the current NUT version as of this writing (2.4.1), `ups.status` is still exposed, with the value "WAIT". Some other values from the `ups` collection are also exposed.

### Using host names for UPS NMC

An UPS network management card may be assigned a fixed/static IP address or a dynamic one (e.g. by DHCP) in your network. Due to this, you may want or have to use a dynamic naming service to access the UPS. Note that this may become a problem specifically during large outages and shutdowns, when your DHCP/DNS server might already go down while the driver needs to resolve the name involved (especially during late-shutdown hooks, when a new instance of the driver program might start just to tell the UPS to power off or to power-cycle).

It may be wise to ensure your OS name service client can cache the UPS name sufficiently long, or to use fixed IP addressing (and an entry in `/etc/hosts` for good measure, so you only have one spot to eventually re-configure this).

## AUTHOR

Arnaud Quette <arnaud.quette@gmail.com>

## SEE ALSO

### The core driver:

nutupsdrv(8)

### Internet resources:

- The NUT (Network UPS Tools) home page: https://www.networkupstools.org/historic/v2.8.5/

- The PowerMan home page: https://github.com/chaos/powerman